My old unit lasted 20 RIP lol.... The outside unit was a 4 Ton and the A/H was a 5 Ton. I guess back then they did that for efficiency. So my question is do I go with a 5 Ton in and out since I am use to a 5 Ton A/H or do I go with a 4 Ton which fits the 2100 sqft that I have?
I've had a few contractors tell me to not go with a 5 ton bc it will mess up my duct system and cause humidity issues...... but is that true when your AH was already a 5 Ton? In my mind if the A/H is what pushes the air then shouldn't a 5 ton be fine for both. This is my first time replacing a system so I am trying to learn while sweating bc its broke.
Help! - Single girl trying to not get taking advantage of. I already know the specs I want for the $2000 tax credit. I live in FL too.
** Forgot to Mention: its a Heat Pump - Split system