Need a refrigerant/oil expert.
Came across a job with an almost new 410a York split system where some hack thought R-22 and 410a were compatible refrigerants, and dumped a few pounds of 22 into it. (Before we knew what happened it hit 700psi high side and destroyed the low side gauge) I can recover, vac, and refill with 410 but the question is, what effect did the 22 have on the oil if any? Has the oil been ruined by adding the 22 and need to be replaced as well?
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
HVAC Site - Professional HVAC Contractors Forum
A forum community dedicated to professional HVAC contractors. Come join the discussion about The industry, safety, ducting, finishing, tools, machinery, projects, styles, scales, reviews, accessories, classifieds, and more!