how on earth do you change a flame rod on a G61mpv. i have been in the trade for 25 years.... residential only a couple of years, who in there right mind engineered this thing ....... whats the easiest way to change it:blink:
I take the rubber boot out/off and then get a 1/4" magnetic nut driver. Do not forget to cover the opening to the inducer, if you drop the screw it is a b!tch to get out easily.
Sometimes, depending on the gas piping, removal of some or all of the manifold and/or piping is required.
When they brought in the G71 and it was the same, we brought in tools for the area rep so he could see the error of their design. I guess they finally listened, they did them different on the newer models.
1 - 6 of 6 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to professional HVAC contractors. Come join the discussion about The industry, safety, ducting, finishing, tools, machinery, projects, styles, scales, reviews, accessories, classifieds, and more!