Have a 2 ton 410a hp running 75 suction & 365 head pressure od temp is 79 degrees suction line temp is 69 and air coming out the vents is 68 degrees and its 77 degrees in house.. Anyone have a clue what my problem is ?????
While the system is running, place the bulb in ice water, should see the suction pressure drop. Then place the bulb in hot water, should see the suction pressure rise. if it does both as I said, its good.
A forum community dedicated to professional HVAC contractors. Come join the discussion about The industry, safety, ducting, finishing, tools, machinery, projects, styles, scales, reviews, accessories, classifieds, and more!